Water supply to the house built
During the construction of the house you have to bring him with cold water. The creation of a plan to carry out such actions will deal with plumbers, who knows the area well and at the same time a nearby business, which supplies the water. The mere implementation of this plan must be performed by a number of people employed in the construction of the house. At the same time you will need to choose the right place to bring a backyard manhole. One of the first works carried out in a newly built home will be performing its water and sewage networks and connecting the boiler, so that the house will also heat water, over time more and more useful. You will also be able to expand a home network plumbing for another connection and install home sanitation.
Boiler basic definition
A boiler is a closed vessel in which water or other fluid is heated. The fluid does not necessarily boil. (In North America the term "furnace" is normally used if the purpose is not actually to boil the fluid.) The heated or vaporized fluid exits the boiler for use in various processes or heating applications,12 including water heating, central heating, boiler-based power generation, cooking, and sanitation.
Accessories for boilers
Pressuretrols to control the steam pressure in the boiler. Boilers generally have 2 or 3 pressuretrols: a manual-reset pressuretrol, which functions as a safety by setting the upper limit of steam pressure, the operating pressuretrol, which controls when the boiler fires to maintain pressure, and for boilers equipped with a modulating burner, a modulating pressuretrol which controls the amount of fire.
Safety valve: It is used to relieve pressure and prevent possible explosion of a boiler.
Water level indicators: They show the operator the level of fluid in the boiler, also known as a sight glass, water gauge or water column.
Bottom blowdown valves: They provide a means for removing solid particulates that condense and lie on the bottom of a boiler. As the name implies, this valve is usually located directly on the bottom of the boiler, and is occasionally opened to use the pressure in the boiler to push these particulates out.
Continuous blowdown valve: This allows a small quantity of water to escape continuously. Its purpose is to prevent the water in the boiler becoming saturated with dissolved salts. Saturation would lead to foaming and cause water droplets to be carried over with the steam ? a condition known as priming. Blowdown is also often used to monitor the chemistry of the boiler water.
Flash tank: High-pressure blowdown enters this vessel where the steam can 'flash' safely and be used in a low-pressure system or be vented to atmosphere while the ambient pressure blowdown flows to drain.
Automatic blowdown/continuous heat recovery system: This system allows the boiler to blowdown only when makeup water is flowing to the boiler, thereby transferring the maximum amount of heat possible from the blowdown to the makeup water. No flash tank is generally needed as the blowdown discharged is close to the temperature of the makeup water.